Hi! Simply click below and type your query.
Our experts will reply you very soon.
|Business Type||Manufacturer, Exporter, Supplier, Retailer, Wholesaler|
|Construction Type||Compartmentalize Non- Compartmentalize/Cubical|
|Type||Manual VFD Panel Auto VFD Panel|
|Max. rated of VFD||400KW|
|Click to view more|
Preferred Buyer From
When a VFD starts a motor, it initially applies a low frequency and voltage to the motor. The starting frequency is typically 2 Hz or less. Starting at such a low frequency avoids the high inrush current that occurs when a motor is started by simply applying the utility (mains) voltage by turning on a switch. When VFD starts, the applied frequency and voltage are increased at a controlled rate or ramped up to accelerate the load without drawing excessive current.
This starting method typically allows a motor to develop 150% of its rated torque while drawing only 50% of its rated current. When a motor is simply switched on at full voltage, it initially draws at least 300% of its rated current while producing less than 50% of its rated torque. As the load accelerates, the available torque usually drops a little and then rises to a peak while the current remains very high until the motor approaches full speed. A VFD can be adjusted to produce a steady 150% starting torque from standstill right up to full speed while drawing only 50% current.